| Exd Stopping Plug: 1" NPT, Brass
PA-D series of Stopping Plugs are used to seal unused cable gland or
conduit entries in Ex approved enclosures, maintaining the hazardous
location certification and the overall integrity of the installation.
Type 'A' Plugs are
designed to be installed from the outside of an enclosure and tightened
with an appropriate hex (Allen) key. When installed they are flush with
the outside of the enclosure wall.
Certified to protection concepts Exd "Flameproof" for use in Zone 1 and Zone 2 applications, the
Redapt PA-D series of Stopping Plugs are approved to the latest
international standards. ATEX (CENELEC), IECEx and GOST-R hazardous
area certificates are available. Additionally, CSA
approval certificates can be supplied to cover use in North American and
Canadian Class I, Division 1 and Class I, Zone 1 applications.
Technical Data Table:
|Protection Method||Exd – Flameproof|
|Ingress Protection Maintained ||IP64|
|Impact Resistance||7 Nm|
|Limiting Temperature Range||-50°C to 180°C (for Group II applications)|
-50°C to 150°C (for Group I applications)
|Standards Approved To||IEC 60079-0, IEC 60079-1, IEC 61241-0, IEC 61241-1|
|CENELEC ATEX Approval||SIRA99ATEX1113X|
I M2, II 2 GD, Ex d I/IIC Mb Gb, Ex tb IIIC Db, IP6X
|IECEx Approval||IECEx SIR 12.0016X|
Ex d I/IIC Mb Gb, Ex tb IIIC Db, IP6X
RU ?-GB.??06.?00106 – Russian
RU ?-GB.??06.?00106 – English
RU ?-GB.??06.?00106 Annex Document – English
|CSA Approval||1248014 (LR 106084-2)|
Ex d IIC; IP54; Class I, Zone 1 & 2 Groups A, B, C & D.
Class I, Division 1 & 2; Groups A, B, C & D; Class II, Groups E, F & G;
Class III; CSA Enclosure Type 3
Data Sheet - Stopping Plugs
Looking for a different size or material? Other Ex fittings?
Please check out our line of Explosion Proof Fittings or call (888) 835-0868